To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I work for a heating company and we are having a problem with a 1 year old rinnai boiler install. The initial install was 3 zones, a 1" zone for radiant and 2 other 3/4 zones and all has been fine. We installed another 3/4 zone for baseboard heat in the basement and now when the new zone calls we get backflow thru 1 of the 3/4 first floor zones and thru the radiant,first floor zone, on the return side. There are conbraco 125s flowchecks on all the returns and all the circulators on the supply side have internal flowchecks. The wiring is fine as only the zone calling energizes and I confirmed with testing the taco zone control and it is fine, so there is a pressure or over pressure issue, the boiler is at 16 psi+-