To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Cat 1 vs Cat 3 - benefits to Cat 3?
Cat 1 appliances are mid efficient non positive vent pressure - non condensing. Cat 3 are mid efficient positive vent pressure, non condensing. If an appliance can run either option (e.g Viessmann Vitorond 200), what benefits are there to running a cat 3 over a cat 1? The only one I now know of is you can run smaller vent sizes on Cat 3 obviously because the positive vent pressure helps push the flue gas out instead of relying on draft to move it. The cat 3 may be slightly safter as it has to be a fully sealed vent where as a Cat 1 in a lot of cases requires some form of draft control (e.g. draft hood, barometric damper) which could spill in some situations. Any other benefits to Cat 3?
Class 'A' Gas Fitter - Certified Hydronic Systems Designer - Journeyman Plumber