To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I have a three zone hydronic infloor system heated by a munchkin boiler. Zones are controlled by two wirsbo actuators and one uponer actuator. One of my zones turned on/opened earlier today and has not shut off despite having satisfied the thermostat hours ago. Thermostat is set at 50 (its a workshop) and room is close to 70 degrees. pump is running constantly. Boiler appears to be turning off and on as it should (dependant upon return temperature). How should I troubleshoot this? Do I likely need a new actuator? Is there something I can do manually for the short term to shut down the heat in that room?
OK so this is what I did. I disconnected every wire that was associated with that actuator. First I disconnected the wires (one white one yellow) from the thremostat communicating with that actuator - the actuator stayed open/pump on. So I discoinnected the other yellow wire and the two red wires associated with that actuator. That worked for now - the pump is off. That actuator is still open which I believe means that that room will get heat when another zone calls - that is a good thing. I have basicly made it a two zone system yes? Until I can get a new actuator. Any feedback appreciated.
0 · ·