To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
triangle tube presitage excellents 110
boiler installed about 5 years ago by company i work for. had to change actuator twice but been running fine. no complaints of noise until now.
customer states unit very loud tenant states never hearing a noise.
upon start up unit makes very loud suction type noise shakes the house. it has both intake and exhaust piped outside 3" pvc. was thinking blocked intake but makes noise with cover off sucking basement air as well.
found noise coming form short intake tube off gas valve. removing this short intake tube cuts the noise down 95%
anyone have this issue or fix this issue, right now the customer is running without that intake tube hooked to gas valve
i remember having this noise years ago on a triangle tube delta. pulled intake air pipe at burner noise went away. the factory had a big parts changing kit to fix that.
0 · ·