To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Installling indirect water heater
I am planning on a DIY install of a Crown MS-40 indirect water heater. I currently use the DHW coil in a Crown 120,000 BTU/hr boiler.
I have the MS-40 on site. I still need to get T/P valve rated at 181,800 or higher, 2 of the Taco Z075C2, 3/4" Sweat Motorized Zone Sentry Zone Valves and to make the MS-40 priority and supply 24VAC for the zone valves I need a Honeywell R8285A Control.
I have been through the install manual and think I meet all the requirements. I only have a few questions:
1. Anything special when teeing off the supply and return 3/4 copper to add the new zone?
2. The Honeywell aqua-stat L7224A currently has a low limit of 180 with the differential of 16 and no other DHW settings turned on. What should I consider for the settings after the MS-40 is connected?
0 · ·