To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
The results were much better than expected; it replaced a waaaaaay oversized UPS32-160F. You could hear it howling like a ghost throughout the entire building and there was no delta T on the supply & return. I gave them a quote on replacing it last winter but they said it was out of their budget at the time, it finally crapped out after about 4 years in service about 3 weeks ago so it became a necessity being a town hall in a small hamlet about an hour away from my own. I generously estimated the head of the system at 16ft. @35gpm but it turned out to be much less than that as you can see in the pic. It's pumping through 1-1/4" convectors in wooden cabinets throughout the approx 10,000 sq ft building. It usually draws less than 32watts and has cost about $2 to run over the last few weeks, compared to the old circulator's 625watts (on speed 3 which is what it was on lol!) I figure they'll have a yearly savings of about $300.
0 · ·