To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
OK here's one we havent seen before. 3/8 heatpex in sandwiched application, between subfloor and 3/4 t&g flooring. The flooring is finished and one of the loops is completely blocked wont pass 120psi air through the loop. inspection of subfloor entry/exit shows no visible kinks or problems. layout of the loop was on 8" centers. With the loop open (no manifold connection) no air will pass at all. Has anyone used nylon fish tape to try and locate a block like this? This would minimize how much flooring to remove in order to locate the block. Loop is about 220ft. Any ideas would be great.
Thanks in advance....