To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Alpine 150 gas boiler at Low temps
Has anyone had any experience with the Alpine 150 Boiler at -50 degrees?
I had a boiler shutdown with error codes that the outside sensor was open so i put a 60 watt light bulb under it and that cleared that. Then I plugged the outside vent and took the front cover off and left it off. The boiler rumbles a bit at start up because the gas line runs 30 feet in black pipe outside above ground so i'm sure the gas was coming in super cold and was a bugger to ignite. Last winter the condensate line froze up so i wrapped it in klawool and that solved that problem. I'm curious if anyone else has operated one of these below minus 40 degrees and if so what did you do different?
Tekpilot (as in teklanika river)