To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Cross reference on Honeywell gas Valve...
After replacing Honeywell valves on boilers after 7 years due to pilot magnets failing to hold, I am switching to White Rodgers for replacements in hopes to getting better service life. A little more cost, but it may be worth it. However, I have not been able to find a replacement valve for the step opening valves that Burnham and New Yorker use. First step is fixed at 0.7 inches and full open is set at 3.5, adjustable 3 to 5 inches. The smaller valve is a Honeywell VR8200C 6008 (1/2 by 1/2) and there is also a 3/4 x3/4 model I need. I use Johnson Controls Husky thermocouples set for 28 to 30 MV open circuit.
The Steam Whisperer (Formerly Boilerpro)
Chicago's Steam Heating Expert
Noisy Radiators are a Cry for Help
0 · ·