Welcome! Here are the website rules, as well as some tips for using this forum.
If you've found help here, check back in to let us know how everything worked out.
It's a great way to thank those who helped you.
Won’t fire unless capacitor housing is unlatched
Hey everyone! First post on this forum! Now that I have multiple properties and about 9 different heat sources amongst them I figure this forum may be a great place to join! So my first problem although not really a problem because this furnace isn’t exactly necessary but I’d love to have it as a backup! So I have this fairly old oil heater in the basement of my 1850 duplex. It had this ancient burner in it that weights damn near a ton! I replaced it with a burner from an oil fired hot water heater that was down there and not being used. I matched everything up swapped the nozzles and checked the pressure and everything else so it should be a modern version ready to go! However I couldn’t get it to fire! Eventually I put the other nozzle in which is .1 gph higher and 10 degrees less then the one it’s supposed to use and it fires right up and purrs like a kitten and I shut it off so I don’t overheat it due to the wrong nozzle being in there. I put a new .50 gph 90 degree hollow nozzle in to replace the old nozzle and still nothing. Adjust the air to no avail but when I unlatch the spark box on the top and bounce it up and down briefly it fires right up and if I leave it unlatched it runs fine and cycles and works great. If I close this latch and add air it won’t start. I would imagine having it unlatched adds air but if I open the air supply no matter how much it won’t fire unless the spark box is unlatched. I’m a bit baffled. If I push the box down to sit flush the flame immediately goes out. Any oil burner folks have any idea what I’m missing?