In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.

# Steam Formulas

Member Posts: 2,668
So, I'm sitting in the office on a Saturday, thinking about steam like usual. Came up with a few quick reference guides for header and vent sizing. This will be a growing list, I'm sure. Feel free to improve my numbers or add to them.

Steam Formulas and Capacities

****Header Size per Maximum BTUH DOE Output****

(Based on Velocity of 15 ft/sec. to 20 ft/sec. and 1 PSI of pressure)

2" Header    = 48,384 - 64,512

2.5" Header = 68,832 - 91,776

3" Header    = 106,416 - 141,888

4" Header    = 183,312 - 244,416

5" Header    = 287,856 - 383,808

6" Header    = 416,016 - 544,688

3&4 Section Boilers = 3" Header

5&6 Section Boilers = 4" Header

****Steam Venting Practical Capacities****

GORTON 1

1-1/2"    @ 25 feet

2"           @ 15 feet

2-1/2"    @ 10 feet

3"          @ 6 feet

GORTON 2

1-1/2"    @ 80 feet

2"           @ 50 feet

2-1/2"    @ 35 feet

3"          @  20 feet
- Joe Starosielec
[email protected]

• Member Posts: 918
steam drums

Bigger boilers sometimes had drums. When I think about it now, I wonder how thermal expansion was accommodated.
• Member Posts: 2,668
MarkS

I used the formulas in TLAOSH and the venting charts. I don't have it on hand right now. I'll post my notes later in the week.

The only numbers I couldn't calculate were header sizing for lower pressures than 1 psi. Your system at 1 oz could probably work with a 1" header!
- Joe Starosielec
[email protected]
This discussion has been closed.

#### Welcome

It looks like you're new here. If you want to get involved, click one of these buttons!