In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I have a Triangle Tube Prestige 250 boiler hooked up to a Smart 40 Indirect Hot water heater. Which T&P relief valve am I supposed to use? The manual seems to have two suggestions - one based on tank size, the other on BTU - but they differ:
Determine T&P relief valve size by the follow- ing specifications, unless they conflict with local codes:
- TR 20/30/36/45 - SMART 20/30/40/50: 3/4”NPT with an AGA Rating of 100,000 BTU/hr. (Watts 100XL-8 or equivalent).
- TR 60/80/100/120 - SMART 60/80/100: 3/4”NPT with an AGA Rating of 200,000 BTU/hr. (Watts 40XL-8 or equivalent).
Also, the Watts 100XL-8 is about $14 from PEX supply while the Watts 40XL-8 is about $130.. Why is there such a difference in price? Something I'm missing?
THANK YOU IN ADVANCE!