In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Just looked at an old Smith 340 Mills boiler. The system has both radiator air vents and steam traps on other radiators. The boiler is set in a pit to maintain the "A" dimension.
The owner does not want to pay for the old boiler removal.
I'd like to install a new steam boiler higher then the old using a simplex condensate return pump and receiver.
? Do I need a steam trap before the receiver tank?
? Should the return piping remain at its current elevation? (in the pit)