In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Alpine MCBA - indirect insltallation
NOT a PRO.
How can i get the Boiler loop circulator to run in either the heating system mode or DHW mode. The MCBA control has one wire for system circulator and another for DHW circulator.
When in DHW mode the DHW wire is energized and not the system circulator wire.
I guess this is for piping the indirect off the boiler loop when only 1 circulator for the indirect and boiler.
I'm connecting the indirect off the header pipe and I need the boiler loop circulator to run in both modes.
Can both these wires be connected to the boiler loop circulator so it runs in both modes.
I'm reluctant to do that because of the electronic control; i don't want to damage it.