In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Unusual Radiator Repair By All Steamed Up, Inc.
This radiator had internal tie rods and gasketed sections.
We had to cut out the 2" recessed plugs at both ends on the top and the end opposite the inlet at the bottom to get access to the internal tie rods.
New EDPM gaskets were installed between the sections and new tie rods and nuts installed. The ends were re-plugged with counter-sunk 2" plugs (a bit hard to find).
It held water at 30 psi for 15 minutes. Eventually.