In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
We have a customer with a AFG in a 68 willy.Hitting reset like clockwork every 12 -14 days. no evidence of delay or excessive oil in chamber on start up. More than one tech has worked on it and have found the same result Nothing wrong. electrodes replaced, ohms on cad cell good, trans good and even replaced just out of frustration. burner has been pulled and set head amps on motor are good. Pump psi set @ 100 psi and holding on shut down. oil line above ground no visible leaks or damage. ???????