To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
the pressure coming into the boiler is 20-22 psi, it seems that the system just need to be purged everything appears to be good now house is getting warmer. I listed all other gauge readings in recent post. Thank You icesailor.
I wish I knew why the Uponor connector failed. It was a clean break in a straight 1" line connector. (Said earlier it was a 1.5") The plumber just said, I have never seen that happened before. The connector had been installed about one year ago. The line is carrying hot water at about 140 degrees and was insulated with the black foam insulation. I am a little nervous about the whole system now. That is why I was looking to install some type of safety or cut off valve on each line going to the air handlers.
My fill line goes into a 80 gallon storage tank and then to the boiler. This provides the hot water for the house as well as hot water to four Lennox air handlers for hearing the house. Therefore if I closed the fill valve then there is still over 80 gallons of water that could be pumped if another line broke.
I have learned from this site that "you don't get what you don't pay for". Ice is overwhelmed with spam. Have a look at www.fastmail.fm to relieve your suffering for a very small fee. I have had no spam since joining over two years ago. Ve get too soon olt and too late schmart, eh! Vibert_C