To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Riello on Buderus Problem
Hello from Beantown, Walligans!
I have installed many Buderus/Riello packaged boilers over the years and they are my boiler/burner of choice. I usually install them and forget about them until they need their anual service.
However I have this one G215-4 oil boiler that I installed a few years ago that is driving me Nutz! When the unit doesn't run for a long time it loses its prime.
It is connected via a single pipe to a Roth tank (about 6' run, tank is outside), has a spin and grin type filter adjacent to the boiler. I have already replaced the flexible suction line inside the Roth tank with ridgid pipe. The fuel pump pressure and suction are fine and the unit runs great until a warm day when it doesn't come on as often.
I am thinking of running a return oil line back to the tank from the fuel pump. I have always run single oil pipe systems and never had a problem in twenty years other than this one.
Has anyone else had this problem? Any constructive thoughts and comments are greatly appreciated
0 · ·