To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
re-piping an old rad system...
I'm looking at a re-pipe job involving an old Victorian-era home heated with cast-iron rads. The system is currently all one zone. I'm re-zoning so that the system has either:
-one zone per room
-one zone per floor (3-5 rads per zone)
I'd like the zoning to be a bit more user-friendly.
Has anyone re-piped a system this way before? I'm looking at a one-zone-per-rad scenario using 1/2" wirsbo HePex to/from each rad, controlled by either a zone valve or a dedicated small circulator.
I wonder, though, will such small zones cause short-cycling of the boiler? It is a non-condensing, cast iron oil fired boiler with domestic immersion coil.
If short cycling could be an issue, I will instead pipe it with one zone per floor (that's 3-5 rads per zone).
In this case I'll pipe reverse/return, or maybe get my hands on some monoflo tees. Not really common around here
My main question is, will the one-zone-per rad setup work, or will there be problems?? Haven't done it before with old cast-iron radiators. Panels yes, cast rads no.
0 · ·