To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Burnham series V1 22 years old
Our boiler is older but the efficiancy has always been excellant (88+%). At some time a 110x60 nozzle was installed and that is how we got it 6 yearts ago. We haven't had any problems untill our tech installed a 135 nozzle (factory recommended) and now every once in awhile when it fires it sounds like the furnace is coming apart. We just had the fire shield replaced acouple of years ago and I fear for it's life. At some time the other night the furnace shut itself down so we woke up to a 52degree house which literally took 12 hours to warm up. Most of the time it fires smoothly but not as quiet as when the 110 nozzle was in it. We also have noticed that the furnace comes on for a shorter period of time and comes on more often than with the 110 nozzel it had. A new oil filter was installed and hasn't made a difference.
Fitzwilliam New Hampshire
0 · ·