To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Flue pipe and foil tape on oil fired boiler
What is the correct type/kind of flue vent pipe for a residential oil fired boiler? New Yorker S-AP, 6" flue , 1.15 GPH.
Reason I ask..... 2 days ago, I began to smell an acrid odor of flue gas in the boiler room. Just a hint. CO detector did not go off, nor did the smoke detector. I even tried a second CO detector in the room to be sure.
So I notice some soot marks around the "ribs" of the flue vent pipe (in the elbow where you twist to get a different angle). The joints of the vent pipe pieces have foil tape on them. So I get some foil tape and tape up the "ribs". 4 hours later the smoke detector goes off and there is a smell of melting plastic. No CO readings on either CO detector. I sniff around and find the sticky glue is melting on the foil tape and THAT is the smell.
OK, (1) what is the correct type/kind of flue vent pipe and (2) do you use foil tape on the seams? If so, I figure there must be a special foil tape where the sticky glue doesnt melt off and smell bad?