To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Exhaust fan in boiler room.
I have what appears to be an easy question but my knowledge of locations of codes are at a loss on this one. Where can I find the code requirements that specifically state you cannot exhaust a boiler room?? I have a job at 4 buildings for the Air National Guard, where they are doing exzctly this. The contractor involved does not believe me when I explained to him the "bad" way of exhausting the air. Believe it or not, in one of the buildings, he interlocked the exhaust fan with the burner operating controls too! And even uses the proving switch for the EXHAUST to be used as a "Running Interlock" I have to show him in print, the error of his ways and I cant seem to locate it in the BOCA book. Anyone out there that can help???? In the words of the Duke,........ Much Obliged. Jeff Krawic