To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Adding supplemental hot water system to steam heated house
The house is 5500 sf 1929 stone colonial with steam heat. Steam boiler is brand new together with all new near boiler piping and works perfectly and silently. Philadelphia, PA locale.
Just don't tell me "if it an't broke........."
From a "what if" hypothetical point of view, lets suppose that I put in maybe half or two-thirds the required radiation, basically whatever size baseboard or radiator conveniently and aesthetically fits the room. (Steam system has recessed convectors with finish plastered fronts-nice stuff from the Warren Webster Company late of Camden, NJ) Then run hydronic with the steam thermostat set well down to come on only if the water can't keep up. Maybe turn the water off mid winter, maybe not. Maybe toss in some hydronic element below the steam convector element inside the Warren-Webster enclosures for a totally hidden effect.
Using an intentionally undersized system would keep the radiation as small as possible so as no to detract from the decor. Plus, I wouldn't run heat to every part of the house. Maybe use pex-al-pex for the water.
My theory: It would avoid running the steam on mild days, saving substantially on fuel bills.
0 · ·