To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I was wondering if anyone has had experience with the Taco Hy Vents leaking. Our hydronic system has the Taco Hy Vents piped into the return on each zone. Long story short, I suspect one of them is leaking as there are clearly water marks on the vent itself and occasionally puddles beneath the manifold in the morning. Seems to happen in the early monring hours as this particular zone is heating up for the day. The funny thing is that this is a fairly new system (4 years old).
I plan on closing the ball valves on each end of the zone, draining the zone, replacing the vent with a new Taco Hy Vent, and then refill the zone. Does this sound right to you folks and have any of you had the similar experiences with the Tac Hy Vents failing???
0 · ·