To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Problem with \"Flashback\"
of a Utica DV50BLP boiler, power vented. After running for a few minutes the gas flame will flashback in the burner, burning at the orifice. There is no air shutter on this burner. If I shut if off and restart it will be fine for as long as 10 to 15 minutes then it flashs back again.
I have the LP gas pressure set at 10.0" W.C. with a 47 drill size orifice, single burner 50,000 BTU's. Specific gravity 1.52 BTU content 2550 BTU's per cubic foot.
This is a side wall vented unit air for combustion from within the building and there is plenty of air as this is a big wide open garage area.
Combustion analysis CO2 9.5%, O2 4.8%, Flue gas temp 250 degrees CO 25 PPM air free.
I have tried everything to solve this problem nothing works. Any ideas?
0 · ·