To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I'm looking for someone to shed some light on a dispute for me. We are in the process of installing a heating system for a new truck wash. The design calls for a single 2" monoflow system feeding approximately 10 hot water unit heaters. I would like to run the piping in copper but my boss wants to run it in black pipe using standard black fittings. How do you do this when there isn't a venturi fitting made for black pipe? He wants to reduce the size of the run on the tee to create flow through the branch. For example, to feed a unit heater with 1" pipe, he wants to use a 2 x 1-1/2" x 1" tee. I don't think it will work, but I may be wrong. Can anyone shed some light on this subject?
0 · ·