To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
i am installing a weil mclain egh steam boiler approx.400,000 btu's i currently have 2- 2inch risers comming up 90 ing towards the back of the boiler then they 90 towards each other to a tee, the bull of the tee feeds the building. i do have a tee instead of a 90 on the horizontal runs for the equalizing line, is it ok for the steam bullhead at the tee,? will it cause water to carry up into the system, the bull of the tee is 3 inch