To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Adding a Radiator to an existing one pipe steam system
I have a well insulated three season room that I am considering adding heat to to extend it's use through the winter.
On the opposite side of the wall adjoining the three season room is a steam radiator. I am wondering if it is ok to replace the current L joint to the existing radiator with a T joint, and then have a pipe added to run from the T joint through the wall to a new small radiator to heat the three season room? The additional piping run would be no more than 2' long. The three season room is approximately 200 sq feet. So in other words I'd have two radiators running off the same pipe.
I am researching ideas as this is a job I'd have to hire out. Which brings me to a second question -- who do I call to work on an older rad steam system? Is this a job for a plumber or should I be looking elsewhere?
0 · ·