To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Heat Load assessment different from quuted Boiler Size
I made heat-load calculations (see attached excel) for the large 3-storey home pictured in the attached photo. We're planning on using the existing hot-water radiators and installing a new mod/con gas boiler.
One quote for the job suggested we get the NTI TFT 155, which has a heating capacity of 144 MBH.
There seems to be a huge difference between my calculation of heatloss (~62,000 BTU/ hr) and what he thought would be an appropriately sized boiler (144,000 bth/hr). Which one of us is off?
What makes me suspect that I might be closer than the contractor was, is the fact that the existing radiators tend to match (roughly) the heatloss calculations on a room by room basis.
0 · ·