To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Twin Steam Boilers - 4 Stages of Firing Rates
So, we just wrapped up another twin boiler setup on a Warren/Webster vapor system. Oil to gas conversion. Since the SMITH 8 is no longer in production, we've been installing a lot of PEERLESS 63 series boilers. The only way we feel good about an atmospheric boiler is by installing a 2-stage gas control valve in them. Robertshaw makes a series 700 two-stage valve that comes in two different sizes up to 720,000 BTUH. Super easy to retrofit and install. The High is 100% and Low is 60%. It's the absolute perfect fit for High/Low on a steam system. As soon as the mains are hot, you can drop out your pick-up factor and run on Low fire until the t-stat is satisfied. On this job, we're controlling 4 separate firing rates. I can maintain 4-8 ounces of pressure with just the Low fire of one boiler.
We installed orifice plates in all of the rads/convectors, as well as upgraded 3 original WW crossover traps. The Air Eliminator check valve is still functional and maintaining a massive vacuum. It takes less than 5 minutes to get 50 feet of main hot.
Each boiler has its own 3" drop header that feeds a 5" system drop header. Dry steam is happy steam!
The picture quality is not great. One day, I'll get some better photos.
0 · ·