To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Two Circs - TT Prestige Excellence
Hello everyone! My contractor friend John and I just finished tearing out my old Weil-McClain that has served my home well for about 60 years and installed a new Triangle Tube Prestige Excellence.
The boiler is in place and running (primarily for DHW now) but I have a few questions about the circulator pump relays using the built-in Prestige controller. The boiler clearly states and supports two CH zones and there are two 24V connections marked CH1 & CH2. We were also under the impression that the boiler supported two zone pumps but now I am not sure.
There is a primary pump factory installed in the boiler that is used for the primary CH loop and DHW heat exchanger (using a three-way valve). This pump is wired to the auxiliary boiler pump terminals. The three-way valve has the line and neutral wired to the DHW pump/diverter valve terminals and another line wired to the CH1 pump diverter valve terminals.
We wired the #2 zone pump to the CH2/system pump terminals and wired the #1 zone pump to the CH1 pump diverter valve terminals (with the line from both the diverter valve and #1 zone pump sharing a terminal. I figured this must be correct because when one of the zone pumps is running, the three-way valve would always be active in CH mode.
The DHW function is working perfectly but when there is a call for heat (from either zone), only pump #2 and the boiler pump run. This would be correct if Zone #2 were asking for heat but the #2 pump runs, even when only Zone #1 is calling for heat. I have tried all three settings on the boiler's CH1/CH2/DHW, CH1/CH2, & CH2 menu but none will run zone pump #1.
Are we doing something wrong with this control panel or do I need an additional controller to support two zone pumps?
Thanks in advance for the help.
0 · ·