To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
lowering steam pressure in a industrial building
Facility was built back in the 1930,originally they had two coal B&W 60K LB/H boilers, time went by and like many others they outsourced part of the production and the steam load was reduced to a mere 20K to 30K LB/H, the coal boilers were scrapped, main pressure dropped from 150pisg to 90psig, now they are planning on cutting steam demand by getting rid of all steam driven production equipment and using the steam for space heating only, currently the steam travels about quarter of a mile from the powerhouse to AHU on the roof and perimeter wall radiation, there are several PRV reducing pressure from 90psi (main) to 12psi to loads. They want to drop main pressure to 12 psi, my first concern was the feed water pumps working outside the curb and the main was sized for high pressure may be too big for the low pressure steam turning it into water before it reach its destination. I would like to know what you guys think before advising the customer against it or perhaps it maybe a good idea and I just dont get the whole picture. thanks!
0 · ·