To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Using condensate pump to shut off Maytag MGF1RC furnace
We just moved into a house with a Maytag MGF1RC100C furnace. It is AFUE 92.1%. Looking at it, I noticed the condensate pump is wired so that if the pump malfunctions, it will cut power to the thermostat and shut off everything.
The basement is unfinished.
I have a couple questions. Is this a condensing furnace? I don't believe it is. If not, does it produce a fair amount of condensate when heating? Our Aprilaire 400 humidifier that should not normally drain water into pump.
I don't want the entire heating system to shut down if the pump malfunctions. Is there a better way to wire it into control board of furnace? Maybe in series with Y wire from a/c?
Would a/c be the main contributor to condensate?