To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Sizing steam boiler with indirect water heater
Hi, I know my new steam boiler needs to be sized to the EDR of the radiators, plus piping pickup, but does it need to be increased for an indirect water heater?
There's a chart on page 8 here, http://www.htproducts.com/literature/lp-83.pdf
but it's unclear to me. I'm not even sure what the units in the chart are or what they're applied to. And there's a note ": IT IS NOT RECOMMENDED TO REDUCE BOILER INPUT WHEN USING DOUBLE WALL TANKS." Meaning the boiler size DOESN'T need to be reduced for those??