To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I'm here with a repeat of a problem I had 4 years ago. (see http://www.heatinghelp.com/forum-thread/130254/Electrical-Problem)
My boiler won't turn on when the thermostats are calling for it. There is a transformer box on the side of the furnace that, if I gently whack it, makes the flue damper open and the boiler will fire. The problem has been ok for 4 years but just started happening again.
Last time I was able to troubleshoot a loose wire inside, and I removed it from a connector and rewired it and it seemed to fix it. I'm kind of clueless as to what to check or how to fix it. Can anyone offer ideas? If I needed to have someone come for a service call, is this something a heating contractor can diagnose and fix or does it need to be an electrician?
Other suggestions from last time were to test the voltage on either side of the transformer and remove and clean the pigtails for the pressuretrol and LWCO. I never did those. I am sort of not sure how to. I have tried whacking the pressuretrol, but that didn't make the boiler fire. Whacking the transformer box did.
Any ideas? Thanks
0 · ·