To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Dual Thermostats - Tell me it isn't so.
Greetings Control Pro's,
I've got an interesting challenge that I am sure someone has a solution for. Redoing an older home with new boiler and five new forced air units. Three of the zones have radiant ceiling heat. Since there is so little cost difference, we are using heat pumps for cooling and secondary heat source. One of the zones has such a small heat gain, we are forced to use a mini split heat pump with the compact ducted air handler.
The problem is, mini split units use proprietary thermostats because the inverter compressors.(Sometimes I think Mini-Split controls are a prank from the Japanese because they lost the war.) So how do I use one thermostat to control the radiant (via circulator relay) and the mini split unit?
0 · ·