To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Help me ballance my 1 pipe steam Please!
Thanks all for posing answers, I have posted a few times and slowly figuring out my 1 pipe steam, to give you some info..I have a 1 pipe steam with 5 radiator on the 1st floor and 5 on the 2nd, years ago a guy from this wall came from Baltimore, put big vents in my basement and told me to get adjustable hoffmans and insulate my basement pipes. I insulated my basement pipes and my 1st floor is now cold and the 2nd is to hot, yesterday i put 2 adjustable vents upstairs and put them on the lowest (slow) venting to slow down the steam to them and on my 1st floor I swapped # 40 with 3 adjustable Hoffmans and put them on the fastest vent, so now this AM, my 1st floor is a little warmer, 2 of the ratiotors seem to click on and off with steam but the one just keeps letting wet steam out, I turned it off and put a new #40 on it and it does the same thing, does not click on and off, air seems to just bleed out, so my questions are as follows
1. The radiator that either hoffman # 40 or adjustable just keeps bleading..what do I do?
2. My thought process of slowing down the steam to the 2nd floor and speeding it up to the 1st is right, right?
3. My oil bills are crazy, I have used 1100 gal of oil this winter, I have a v8 Burnam installed 9 years ago, any new steam furnaces anyone reccomends? Ideas on changing over to Gas?
0 · ·