To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Pickup factor. Help me understand
I'm a bit confused by the use of a 33% pickup factor.
The way I see it, with your piping insulated as it should be the piping should dissipate a fairly small amount of heat. Now in my system my pickup factor is something like 31,000 btus. Once the piping is hot I could see it dissipating maybe 5000btus through the insulation, but 31,000?
So my question is, why do we need a 33% pickup factor if all of your piping is insulated? Wouldn't something like 5% do just fine?
Is the 33% there to makeup for missing insulation and poor venting? Is it simply a fudge factor and not actually necessary if everything is perfect?
Single pipe quasi-vapor system. Typical operating pressure 0.14 - 0.43 oz. EcoSteam
ES-20 Advanced Control for Residential Steam boilers. Rectorseal Steamaster water treatment
If you even insult my steam system in a dream, you better wake up and apologize ò¿ó
Steam system pictures updated 1/25/15.