To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Heat gain in computer server room
Room is 12 x 8 surrounded on all sides by 70-72 degree conditioned space. Ceiling is at least r-30. The electrical load in this room is less than 26 amps X 250 VAC which equals 6,500 watts X 3.414 = 22,191 BTUH of heat gain from electrical equipment. Would 30,000 BTUH cooling be adequate? I'm just the electrician on the job, but this has sparked my interest. A 42,000 btuh Mr Slim mini-split is to be installed and the results should be interesting. I know the inverter system will ramp down to low speed, but is there a limit of oversizing that this may not work for. Meanwhile I keep quiet and again the local yocal knows nothing. Will we have the "cold and clammy" feeling??
0 · ·