To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I'm trying to determine if the F6 head that is currently on my New Yorker FR-122 boiler (circa 1989) is still OK now that it's been downfired to the same as an FR-98 (1.00 nozzle down to 0.85). This thing seems way oversized; even with the 0.85 nozzle it's been running about 6-7 minutes at a time 4 times an hour even with the outdoor temp10 degrees below design temp for this area (approx. 10 degree F). The oil service company installed the nozzle at the annual cleaning after I mentioned how the boiler seemed to be short cycling. But based on info I've read in this forum the stock F6 head may be incorrect for the 0.85 nozzle. I have noticed soot dust around the stack damper and on top of the boiler and the damper slams shut during most start ups (which it didn't do before). So, should I be concerned about this? I'd like to have this thing run fine tuned rather than just in the ball park. Thanks for your time.
0 · ·