To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
This is my dad's furnace that keeps having pressure switch failures. Altitude is 1900ft and the pipe length and 90 count is near the max recommended by the manufacture.
What are the chances this is what is causing the pressure switches to fail or what are the chances the inducer is getting weaker with age? This is a 80k input Luxaire furnace from 2006 running on LP gas.
The first switch lasted 3 years and all of the new ones have only gone a year or so. He would call the installer back out but his concern is the guy will just install a new switch and leave everything alone. The furnace will give an open pressure switch error which will go away if you tap the switch with a screw driver handle. Replacing the switch fixes the problem for another year but seems wrong to keep happening.
Should this be repiped using mostly 45s, or even enlarged to 3" pipe? Is there any reason not to use 45's and have the pipe on an downward angle back towards the furnace? If it should have a new inducer installed, or be repipped he is willing to get it done but wants to know what to do.
As always I appreciate your help! Welcome any and all opinions.
Single pipe quasi-vapor system. Typical operating pressure 0.14 - 0.43 oz. EcoSteam
ES-20 Advanced Control for Residential Steam boilers. Rectorseal Steamaster water treatment
If you even insult my steam system in a dream, you better wake up and apologize ò¿ó
Steam system pictures updated 1/25/15.