To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
allot of times when checking drafts on furnaces, I find the draft pressure to be higher than it should be. I know ideally we are looking for about a ,-04" draft on a conventional induced draft 80% furnace, but what would you do if the draft was higher? What if the draft was anywhere from - .05 - .15? If you check the sizing of the flue is right, if the gas pressure is right, how do you correct this? Could you put a barometric damper in the flue and adjust it with that? I'm just curious to see what you guys would do if this was your job? Obviously the furnace would work more efficiently if you could slow the combustion gases down where they should be so that more heat is extracted from them. What would you do?