To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
HVAC Electrical Bard Unit
Dec 31 2013
Happy New Year~! You are my fellow party people....
anyway, need some help with breakers on a single phase Bard furnace. The main breaker(s) block inside the unit has a bad breaker(one of two) that wont come out of the assembly. It has a 60 Amp 2 pole sq D QO breaker bolt in with a tandum 30 Amp Same. The job is commercial 1 1/4 hours away one way. I wanted to get the entire assembly from Bard but it is 6 weeks out.
There are input lugs for L1 + L2 on the right fed from a 90 Amp breaker inside, with the 2 breakers on the "block" to the left of the lugs.
I proposed putting a 100 Amp weather proof box with 2 breakers to the side then running everything back into the Bard unit which gets expensive + was denied.
Surely some one has something that will hold the 2 breakers that I can mount inside the existing equipment main control cabinet to feed this 15 KW furnace.
I have thought about a fuse block like you see on a fan coil but have no new or used fan coils in stock. (Maybe could pursue that Thursday??
Hope you are having a good time tonight. My wife went to bed at 10:30, so think I will join her.
Bob's Htg West Point IA 52656 319-795-0822
0 · ·