To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Hoping someone can help. I have a fairly new furnace that heats my home through baseboard/radiant heat. Just a few days ago, I woke up to a cold home due to the relay tripping on the Honeywell Ignition control (R8184 D). So, I pushed it back in and it ran for about a minute then popped again. I waited about 15 min and it fired up and ran until it reached its' target temp (180 F). Everything seemed fine. It ran for a few hours. We left the house and when we came back, the relay was popped again and the temp gauge on the furnace was all the way down to 60F. I started it back up and it got back up to operating tempo again. Last night (sometime while we were sleeping) it did the same thing again. I also have an Aquastat Relay Type 8 . The oil burner I have is a Beckett Model AFG. ...O, I have also inspected the cad eye and didnt see any damage or dirt on the lens. Any advice would be GREATLY appreciated!
0 · ·