To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Heat exchanger split after 4 years, misadjusted burner the cause?
We've just been notified by our furnace repair company (who is also our oil dealer) that our heat exchanger in our 17 year old Heil forced warm air furnace needs replacement. We replaced the heat exchanger, at our cost, 4 years ago since there was only a 10 year warranty on the original at the time.
The furnace has been fine all season long. No fumes in the house, nothing. Somehow, however, that changed when they came to do the annual furnace cleaning. After the service person left the furnace stopped working some hours later. 3 service calls later, waking up at 3 a.m. to a house full of oily smelly fumes, a number of additional cleanings and adjustments of the nozzles, we find out that the heat exchanger has split along the seam where it is bolted together.
Is it possible that a poorly adjusted furnace can overheat or otherwise cause the exchanger to split? We are perplexed that our heat exchanger should break after only 4 years, and suspicious that a poor servicing has damaged our property.
Thanks in advance,
0 · ·