To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I m at a house trying to figure out why 2 baseboards on the third floor wont get hot. . There are 3 baseboards, fed by three seperate supply and return risers. One works perfectlywhile the other 2 wont heat. Ive bled them both out and one will heat up slightly then cool down while the other wont get past lukewarm no matter what i do and ends up cooling down. I checked every radiator beneath and theyre working fine. I changed the circulator pump(return side) because the previous one was dead and i added a spirovent near the supply side of the boiler. The only thing i noticed there was no check valve on the return side. Oh ya, the whole system is one zone as well. Is the lack of a check valve on the return causing circulation problems for the 2 cold baseboards? Any help is appreciated. Thanks