To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Buffers on Air to Water HP
Hi there: I'm sorting out the options of an air-source hydronic heat pump supplying radiant floor heat and hi-wall fan coil cooling (choices are Daikin Altherma & Aermec, feel free to opine). We will likely use Aermec hi-wall fan coils either way, though I am checking into Magic Aire or some such. I have a fair bit of experience with Fujitsu mini-splits and hydronic heating, but have never done a hydronic heat pump.
I am curious about people's opinions about buffer tanks: the piping diagrams provided by the manufacturers are starkly different, with the Aermec plumbed directly into a buffer tank (min. 30g), with the loads pulled out the other side, generally with a primary-secondary arrangement with priority DHW pulled aside with a 3-way valve. Altherma provides much less explicit diagrams (that I've found so far anyway) that don't mention buffer thanks, though I've heard it suggested that at least a few gallons would be required to assure a successful defrost cycle.
I don't love the buffer tank in the middle of everything approach, it feels like it's a lowest-common-denominator approach, though I can see how it might provide the most level demand from the heat pump, and perhaps simplify controls too (not inconsequential with 4 radiant zones and 7 air zones, overlapping). My natural inclination would be to put a buffer in-line after all the secondarys (and not in the DHW loop). I'd be very interested to hear others thoughts.
Quick system details: very low-demand house, around 2 tons cooling, roughly equivalent heat. 4 underfloor radiant floor zones, and 7 hi-wall fan coils, 2000sf. Heating is primarily via the radiant, though the fan coils will be available to speed up heating. I'm thinking I can avoid tempering for the radiant: I can run the radiant as high as 100-110F, and even at those temps there's actually a fair bit of heat available from the fan coils, though the DHW will want hotter IMO (the heat pumps can deliver somewhere around 130F). There will be resistive backup on the DHW, and probably within the unit itself for space heating, though we are hoping to never use it (our design heating temp here is around 11F, and both these units can meet the demand at that temp).
Anyway, thanks for any helpful thoughts/feedback/criticism.