To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Hey everyone.... This question is regarding a snow melt system with a mixture of 30% glycol....from the manifold through the 5/8" pex loops (6 of them) the GPM for all 6 of them is 6.84 GPM(1.14GPM per loop)....The head loss for the MANIFOLD is 4.5 ft HD....my question is how do I figure the size of the pipe from boiler to manifold (snow melt load=81,225 btuh/h) do I use 1"?....and how do I find the head loss from boiler to manifold, and do I add it to the 4.5 ft hd from the loops?....need this to size pump...thanks Paul S
0 · ·