To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I want to add a small Modine heater to the return line of a new Modcon install, purpose being to add some heat to a basement area, and knock down the delta-t some more. The old boiler use to keep the basement warm, with it gone, going to get chilly. The Modine will operate when ever the upstairs calls for heat. What is the best way to add the heater to the return line, without messing up the return flow to the boiler? The heater has .5 pressure drop at 1.3 gpm, my return line is 1", with about 5 gpm, serving a 2 split loop system. Thanks in advance for any help.