To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
A local store owner has a 2 door and a 3 door 'zero zone' reach in coolers both running off of the same compressor using 404A. I am being asked if I can take his 2 door unit out due to him expanding a room and he's in need of the space not the cooler. The compressor is sized for the both and basically the 3 door calls and they both get cooling. Other than the compressor being oversized is there anything I'm not aware of if I cap off the 2 door and get it out of the circuit? Each reach in has its own expansion valve and defrost. Thanks in advance.
0 · ·